Classified and labeled by Underwriters Laboratories, Inc.® and Underwriters Laboratories of Canada. Covered under UL File No. R-19207 for frames with 20/45/60/90 minute ratings. Frame tests performed in accordance with UL 9, ASTM E2010, NFPA 257. Door tests performed in accordance with UL 10B, UL 10C, ASTM E2074, NFPA 80, and NFPA 252. Approved for use in New York City: MEA 426-04-M.
Note: This product is not intended for use in locations requiring a barrier to radiant heat. This product does not meet test standards ASTM E-119 or UL 263. If your jurisdiction requires "barrier to heat" framing, please see our Heat Barrier Series.
Maximum Allowable Size Information
|Rating||Max. Exposed Glass Area Per Piece||Max. Exposed Glass Single Dimension|
|20 Minutes||6,396 in2||106-1/2"|
|45 Minutes||4,500 in2||95"|
|60 Minutes||5,605 in2||95"|
|90 Minutes||2,627 in2||56-1/2"|
|Rating||Max. Single Door Leaf Size||Max. Exposed Glass Size Per Piece|
|90 minutes||42"*96'||36" x 56-1/2" (divided lite door)|
All door hardware for Designer Series doors is supplied by Technical Glass Products. Please contact Technical Glass regarding your individual hardware requirements.
Standard door hardware package may include:
To obtain CAD files of any of these detail drawings, please use our CAD request form.
To obtain BIM Models for this product, please use our BIM Model request form.
Download a PDF of our Care & Warranty Brochure.